Electric connection only
Completed by a chap claiming to be a registered 'electrician'
Earth sleeved live but connected to earth in the consumer unit
Loose connections left unchecked are potential fires
Open top surface on consumer unit and un-glanded armored cable
Downlight installed IN the floor timber - fire hazard
Not how you gland an armoured cable
Live cores exposed in roof after box dropped on cable joint
Loose connection melted cable to cover
To the left is a small selection of images from EICR's collected since I started on my own.
Underfloor heating element and insulation.